Re-roofing encompasses both primary membrane replacement and replacement of the entire roofing assembly above the structural deck.
Due to the unique nature of re-roofing, relief from the Warranty Certificate standard may be requested. When relief is requested, applications shall be made in a written submission to the ARCA Warranty Ltd. Technical Committee. This request for relief is termed a “Variance Request” and must contain all pertinent information explaining why relief is being requested.
The Warranty Certificate standards, as itemized in this manual, are applicable to re-roofing as well as new construction, with the exception that the existing drainage slope may be retained in a conventional membrane design if less than 1:100 (1/8"/ft.).
Sheet metal flashings, including lead flashings, adhered to the primary membrane shall be replaced with new materials. Base and cap flashings may be reused provided they are in good condition, fabricated to the Warranty Certificate standard and fit properly.
The Warranty Certificate can only be issued on self-contained roof areas. Control joints may be required to create self-contained roof areas when partial roofing system replacement is carried out. Special attention to drainage provisions may be necessary.
Roof mounted equipment may need to be removed and reinstalled to facilitate replacement of the roofing system beneath them. Equipment mounted on properly constructed curbs of sufficient height may not require removal.
A minimum clearance of 100mm (4”) shall be maintained between the underside of service lines and the surface of the completed roofing system.
When an existing roofing systems is of a different bitumen type than the new system to be applied (e.g. Coal tar pitch to asphalt), care must be taken to ensure that the two dissimilar bitumens do not come into contact with each other.
In some instances there may be two (2) roof systems one above of the other, over an existing roof area. Where two (2) primary membranes are present, both primary membranes shall be removed.
Prior to reroofing, all damaged or deteriorated decks and substrates shall be replaced or repaired with similar materials.
Existing BUR, SBS modified bituminous or hot rubberized asphalt protected membranes may remain in place and serve as the substrate for the attachment of a replacement modified bitumen protected membrane design provided that the existing membrane is prepared by removing any wet or deteriorated material, dust, dirt and debris and primed with a compatible primer.
Existing modified bitumen flashing membranes, when properly adhered and primed with a compatible primer, may remain in place and serve as the substrate for the attachment of a two (2) ply torch adhered modified bituminous membrane flashing. Loose and deteriorated flashing membranes must be removed or covered with an accepted membrane flashing substrate.
To qualify for an ARCA 15 Year Warranty Certificate, only new drains shall be installed equal in size to existing roof drains.
MB-10.2 Primary Membrane Replacement
When considering an existing conventional insulated roofing system for primary membrane replacement the following factors require evaluation:
The affect that the lack of a vapour retarder may have had on the failure of the existing membrane,
The type, condition and thickness of the existing insulation and the amount of moisture that may have infiltrated the insulation (dryness),
The existing roof deck type and its structural integrity, if moisture reached the deck, and
The attachment of roofing system components to their existing substrate(s).
When membrane replacement is undertaken, uncorrected defects hidden from view, such as wet insulation or deteriorated deck, could jeopardize roofing system performance.
Wet and damaged insulation shall be removed and replaced with new insulation, to match the existing thickness.
Care must be taken to ensure all wet insulation is located and replaced.
Under no circumstance shall a phenolic resin insulation product be left in place or reused.
Existing wood fiberboard, mineral/perlite, glass fibre or Stramit primary insulation may be left in place whether or not they are covered by a secondary insulation/cover board.
Existing polyisocyanurate, urethane, foamglass, cork, expanded polystyrene, glass fiber less than 38mm (1.5”) thick and extruded polystyrene roof insulation less than 38mm (1.5”) thick must be removed and replaced, except when covered by a secondary insulation/cover board consisting of wood fiberboard or perlite insulation. Exercise extra caution to ensure that all wet primary insulation is located and replaced when there is a secondary insulation/cover board in place.
When the primary membrane is being removed from stramit or glass fiber insulation that have a facer, the condition of the insulation facer after the tear off determines the surface preparation method for the application of the new roof membrane. When re-roofing over stramit the first layer of approved coverboard must be mechanically fastened to the structural joist or deck. If the first layer is fiberboard, then the second layer of approved 12.7mm (1/2") coverboard may be adhered or mechanically fastened with screws and plates. When thermal upgrading is required, the first layer of the secondary insulation/coverboard may be substituted for/by the upgraded insulation material. Attachment requirements remain the same.
Regardless of the primary insulation type or the presence of an existing secondary insulation/cover board, in all cases, a new secondary insulation/cover board layer meeting ARCA Warranty Certificate application standards is required to provide a consistent substrate for the application of the new roof membrane.
Polyurethane foam adhesive may NOT be used to adhere insulation or coverboard to existing fiberglass insulation, perlite insulation or stramit.
MB-10.3 Roofing System Replacement
After tear-off the exposed substrate shall be inspected for deterioration or damage and repairs undertaken prior to the application of the replacement roofing system.
Control joints, parapets, curbs and roof/wall junctions shall be adjusted to comply with the minimum height requirements for new construction.
For conventional and combination designs, the application of a vapour retarder is a requirement whether or not the original roofing system contained a vapour retarder membrane.
An existing vapour retarder may be left in place if well adhered. Any wet or damaged membrane shall be removed and an additional one (1) ply of felt adhered with hot bitumen shall cover the entire membrane surface.
MB-10.4 Protected Membrane Design Re-Roofs
A five (5) year Warranty Certificate may be issued for Protected Membrane Design re-roofs, when roof drainage slope is less than 1:50, provided that the replacement membrane is inorganic and the field of the membrane is either covered with Type 4 primary insulation incorporating drainage channels on its underside or by an accepted inorganic drainage mat placed between the primary membrane and the Type 4 insulation.
When primary membrane replacement occurs over existing insulating Stramit or rigid glass fiber roof insulation, inspection of the exposed insulation by an ARCA Accepted Inspector is required at the time of tear off, for both rural and urban projects. Additionally, if there is a history of leaking, the inspector shall perform moisture meter or cut tests, one (1) for each 1000 ft² of insulation area. These quality assurance inspections shall be in addition to the normal inspections required for Warranty Certificate issuance.
ARCA administration shall be notified of the condition of structural stramit decks prior to re-roofing.